Shielding effectiveness (SE) test following the Standard NSA-65-6 now superseded by the NSA-94-106 describes general specifications radio-frequency (RF) shielded enclosures for communications equipment.
NSA-65-6 - MEASURING THE EFFECTIVENESS OF ELECTROMAGNETIC SHIELDING ENCLOSURES
The NSA 94-106 (formerly NSA 65-6) is known as the parallel setup, where both transmitting and receiving antennas are in parallel planes, and parallel with the plane of the sample under test.
To perform the following test we need the equipment:
- Continuous wave (CW) source, 1 KHz to 10 GHz.
Transmitting and receiving magnetic field antenna set covering 1 KHz to 1 MHz.
Transmitting and receiving electric field and plane wave antenna set covering 1 KHz to 10 GHz.
Receivers or spectrum analyzers covering 1 KHz to 10 GHz with adequate dynamic range to measure the attenuation.
The magnetic and electric field attenuation tests shall be performed with the antennas located directly opposite each other and separated by a distance of 61 centimeters (24 inches) plus the wall thickness.
Magnetic field attenuation shall be measured at 1 kHz, 10 kHz, 100 kHz, and 1 MHz.
Electric field attenuation shall be measured at 1 kHz, 10 kHz, 100 kHz, 1 MHz, and 10 MHz.
The plane wave attenuation test shall be performed with the transmitting antenna placed at least 6 meters away from the enclosure surface (where practical) and the receiving antenna set no closer than 5.1 centimeters (2 inches) from the wall.
Plane wave attenuation shall be measured at 100 MHz, 400 MHz, 1 GHz, and 10 GHz.
Attenuation tests shall be performed around the entire door frame, air ducts, filters and through any accessible joint or penetration.
In addition, the magnitude and location of the maximum signal level emanating from the enclosure shall be determined by testing at least four locations.
The selection of testing locations should include not only walls, but also the floor and ceiling.
Emctest Technologies is a laboratory that performs shielding effectiveness tests on site
, directly to the customer, in Italy and in Europe
, or at its headquarters in Rimini - Italy.
We perform shielding effectiveness tests for several sectors:
Typical shielding effectiveness measurement frequencies are: 10 kHz, 100 kHz, 1 MHz, 10 MHz, 30 MHz, 100 MHz, 500 MHz, 1 GHz, 10 GHz, 18 GHz, 26.5 GHz and 40 GHz.
Our lab test can perform shielding effectiveness measurements up to 50 GHz.
Read more about it going back to the home page. Or if you are looking for a lab in order to test your product contact us via email or by phone simply clicking here.
Measurements are made according to customer specifications or in accordance with the main standards as below: